SAPL (Auxiliary Source for Delivery Station)
NFC 13-100 compliant
In accordance with the requirements of the NFC 13-100 standard, in delivery stations established inside a building and supplied by a 2nd category public distribution network where protection is ensured by an indirect relay, an auxiliary power supply may be necessary to ensure the operation of the protection or power limitation device and the opening of the circuit breaker or the switch-fuse combination.
According to § 534.1 of the standard, a device must be provided which interrupts the operating circuit when the absence of AC voltage is of long duration (> to ½ hour, for example).
The power supplies proposed in this range are in conformity with this destination and with the reference rules and include in particular the device required by the NF C 13-100 standard:
Time limitation of the battery discharge ( 30 minutes, 1 hour, … ).
Restoration, by pressing a push-button, of the output voltage of the power supply.
Use of the additional energy reserve in the battery for restarting.
24Vcc – 48Vcc en standard
Au plomb étanche
Cf. fiche technique
|Type de produit||
uninterrupted power supply